Upload your photos, chat, win prizes and much more
Can't Access your Account?
New to ePHOTOzine? Join ePHOTOzine for free!
Upload photos, chat with photographers, win prizes and much more for free!
Hi everyone, does anyone out there know much about power showers? We have a Triton AS2000xt power shower and eveytime the isolation switch is turned on it trips the RCD and most of our electricity goes off. The electricity is fine if the shower is isolated. Does anybody know the likely cause and if its a replaceable part or new a shower?
Ps...this is a power shower (built in pump) and not an electric shower
Join ePHOTOzine for free and remove these adverts.
Neutral to earth short somewhere? Possibly a noise suppression capacitor gone short?
Thanks for your answer. Will check during this week. I wasnt sure if somebody else might have had the same problem and known if a new shower was needed. I will bear your answer in mind though and thanks again for the reply.
Good luck! This site offers spares: http://www.showerdoc.com/triton-as2000xt-power-shower-spares
I've not tried it myself and I'm sure there are suppliers.
Try isolating it at your consumer unit (remove fuse/flip the breaker) and try measuring resistance of neutral to earth and live to earth on the shower side inside the isolating switch. Then try working forward to trace the fault. Do be careful and use a voltmeter to verify that the circuit is properly isolated at the consumer unit. If in doubt, GAMI.
does the shower have an on/off switch (in addition to the isolator)? If it has then turn it to off and turn the isolator on - if the RCD trips then the fault could be in the isolator switch.
Thanks everyone. I think if its not a case of simply just replacing a part I will leave the electrics to an electrician though. I'm ok swapping a part but thats about my limit and I dont want to risk making a mistake. Hope I dont sound ungrateful as your input really is appreciated.
There's a good reason why electrical work in kitchens and bathrooms must be done by an electrician who has a P certificate.
Quote: There's a good reason why electrical work in kitchens and bathrooms must be done by an electrician who has a P certificate.
Yes, It's a great money making scheme for local government and regulatory bodies. As far as I remember, part P still permits simple repairs.
ePHOTOzine, the web's friendliest photography community.
Upload photos, chat with photographers, win prizes and much more.
You must be a member to leave a comment
This month's sponsor
Get the latest photography news straight from ePHOTOzine in your email every month and win prizes!
1st June 2013 - 30th June 2013
Check out ePHOTOzine's inspirational photo month calendar! Each day click on a window to unveil new photography tips, treats and techniques.
View June's Photo Month Calendar